ALTISTART 46 MANUAL PDF
Description: This users manual for Altistart 46 soft start motor controllers contains installation, setup, operation, and maintenance instructions. User’s manual ATS46, 9/21/18, English, Spanish, French, pdf MB. Data Bulletin. Cross Reference Guide for ALTISTART® 46 Soft Start Motor. User’s manual UNI-TELWAY ATS VW3G, 12/13/17, English, pdf MB. Programming manual ATS VW3G, 12/13/17, English.
|Published (Last):||10 January 2014|
|PDF File Size:||5.19 Mb|
|ePub File Size:||20.1 Mb|
|Price:||Free* [*Free Regsitration Required]|
Use the fixing points to run the cables along the insulating dividers and connect up to the clips. For units with two transformers only altistsrt right-hand transformer viewing the unit from the front is to be removed. Synchronisation connectors absent or wrongly positioned.
VW4G Moreover, all spare parts are also delivered with instruction bulletins. Value kept for the altistqrt voltage 2 V AC Seco nd ar y: Low torque at start tQ0.
Altistart 46 Soft Starters
Screws Fan view from above 9 – Disconnect the two power wltistart wires from the transformer from the fan black wire with white cable end. For floppy disc 2, follow the instructions that will appear on the PC screen. Assembly size 4 Parts list Interconnection drawing Part 5: Place it at the top of the bracket, in the correct location.
Check correspondence between motor and starter. Fan 2 3 0V 1 8 5W Recommended torque load for screw M4: Humidity test according to IEC and 3. Kanual one thyristor in short-circuit. Assembly size 5 Parts list Part 6: Reference Rated ef f. The motor starts if a altiwtart control is on TBS value equal to 0 during powering up, even though its value is different refused of to reset to zero the parameter TFR hourmeter when the engine is running on-factory adjustment of parameters IPR, TPR and TBS local mode used only upon the first product powering up assignment of LI to LII motor preheating manuaal LIH faults inhibition default startup time when loaded went to 4 seconds removal of the starter thermal protection calculated by the software on C11, C17, C21, C25 and C32 calibre readjustment of the rated current value by on-factory setting A for M12 calibre correction of the anomaly concerning the micro controller upon unshunting with the bypass function correction of the anomaly following a simultaneous altistagt instruction with a stopping instruction.
Altistart 46 Soft Starters – Documents and Downloads | Schneider Electric
SY3CM 14 2 clips: Position the four screws which attach this part. White Red Red White Remove the fan turbine by removing the 6 fixing screws 8 mm spanner. The pump transformer must be removed. Proceeding for on-site test of characteristics dispersion of Altistart 46 thyristors leakage current: OLF acknoledgement, followed by a start request are done as following: I C 10 1 0 3 6 7 17 18 5-point socket: Connect the connector of the current transformer cable to J 43 on the electronic card, observing the wire coding.
Assembly size 1 Parts list Part 2: J7 Connector if pump unit J9 J10 J11 rear view of the control module 5 – Remove the connectors from the vigitherm and the current transformers.
Reassembling as an Altistart 46 1 – Reattach the transformer using the four fixing screws, with the cabling on the left-hand side of the unit.
Conversion instructions for size 3 9 – Install the connectors in the locations behind the control module of the Altistart according to the markings. SY3KC 2 Black wires marks 14 and The time of delivery of the repaired or new element will be given by the dealer or the agency.
Transformer complies with U. Please refer to page 7 for the wiring of the customer terminal block. Phase rotation fault assignment Function Phase rotation detection PiF Phase rotation state The function is active at each start order. Measurement card Screws Brackets 7 – Remove the fan cover two screws altistrt a 7 mm spanner.
User’s manual ATS46
M Has to be fixed on one of the assembling screw before soaking Red wire mark 4: If, for practical reasons, you do not want to disconnect the protection and control circuits, top to bottom terminal resistance can be measured. It performs successive tests of network frequency measurements, filtering of result around 50 or 60 Hz, iteration till decision will be made: Connect the cables to the plug-in units according to the following drawing.
External fault order Operating state Up to now experience: No wire out of the transformer lower part 2 mm minimum mandatory Outlet order is not important.